Zhangjiagang Wilford Thermal Co.,Ltd
ADD: No.5 Nanyuan Road Economic Development Zone Zhangjiagang, Jiangsu Province 215618 P.R. China
Address: No5,Nanyuan Road Economic Development Zone, Zhangjiagang
Free after-sales service telephone: 86-512-58170166
Agency in Shandong
Address: No.1515-1517,Dongsheng Office Building,Longdu Street,Zhucheng city,Shandong Province
Address: Beirut - Lebanon AI Dora - Mar Youssef Street Joumayel Building - 1st floor Lebanon
Model NO.: WNS
Fuel: Gas-Fired, Oil-Fird, Diesel-Fired
Structure: Fire Tube
Water Circulation: Natural Circulation
Burning Style: Fluidized Bed Furnace
Evaporation Capacity: 1 - 20t/H
Rated Steam Temperature: 184-193
Boiler Volume(M3): 3-22
Burner: Unigas, Baltur, Oilin, Weisaupt, etc
Typical User: Food and Textile and Hotel and Oil Field
HS Code: 8402120090
Function: Steam Boilers
Installation: Assembled Boiler
Media: Steam and Water
Drum Placement: Horizontal Boiler
Manufacturing Level: A
Rated Working Pressure(MPa): 1.0-1.25
Heat Efficiency (%): >90
Fuel Available: Light Oil, Heavy Oil, Natural Gas, etc
Export Markets: Global
Transport Package: Seaworthy Packing
Rated evaporation capacity(t/h)2468101520
Rated working pressure(MPa)1.01.251.251.251.251.251.25
Rated steam temperature184193193193193193193
Applicable fuelLight oil,heavy oil,natura gas,liquified gas and urban coal gas
Extemal sizeLenght A(mm)5084602271517600836090509650
Boiler weight (t)7.212.617.218.623.536.245.5
Diamater of main steam opening(mm)65100125150150200200
Industrial Gas-Fired & Oil-Fired Fire Tube Hot Water Boiler or Steam Boiler
Automatic oil or gas fired boilers series WNS have two types. One is steam boiler, and the other is hot water boiler.
1. The capacity of steam boiler is 1~10t/h, working pressure is 0.7~1.6MPa.
2. Output of the hot water boiler is 0.7~7MW, water service temperature is 95degree or 115degree, water return temperature is 70degree.
3. This series of boilers are adopted the structure of horizontal, internal-combustion, three-pass and full wet back.
4. The combustion chamber consists of corrugated internal furnace and wet smoke box.
5. The fuel oil is atomized and injected from the burner into the combustion chamber where it's burnt into smoke of high temperature.
6. The smoke enters the second pass threaded smoke tubes after the radiation and the convection heat transfer occurred in the furnace and the smoke box, then it's back to the third pass smoke tubes, and proceeds with the convection heat transfer again.
7. At last it passes the rear smoke box and is dispelled via the chimney.
With rich experience in design and manufacturing technology of product, strong technical power and reliable product quality, as well as perfect quality assurance system and scientific management mode, Runli Company will assure you to use Runli Brand heat transfer oil boiler and various chemical mechanical equipments safely. If only there is need, we shall serve you wholeheartedly to ensure you be free away from troubles.
Promise before sale: We shall help user to choose boiler type for the most economic and appropriate product, keep it meeting the requirements on technology flow or special design of client, provide user various technical consultation and related information, make on-site visit, design place for equipment, involve in fundamental construction, train stoker in accordance with user's requirements on structural features and performance of equipment.
Promise after sale: We shall guide on how to install, debug, make regular visit to know about application condition of product, provide spare parts for the one easy to wear and damage, standard parts and fittings forever. With 24 hours' service telephone, all users can call us when equipment is in trouble, our technicians will be on-duty around clock to deal with any problems, and then solve your future worry if having.
Warranty: one-year commitment to bear the cost of repair produced by manufacture reasons.
Replacement: free replacement for severe quality problems found within one year.
Return boilers can be returned if severe quality problems were found and boliers has been replaced within 6 months.