Zhangjiagang Wilford Thermal Co.,Ltd
ADD: No.5 Nanyuan Road Economic Development Zone Zhangjiagang, Jiangsu Province 215618 P.R. China
Address: No5,Nanyuan Road Economic Development Zone, Zhangjiagang
Free after-sales service telephone: 86-512-58170166
Agency in Shandong
Address: No.1515-1517,Dongsheng Office Building,Longdu Street,Zhucheng city,Shandong Province
Address: Beirut - Lebanon AI Dora - Mar Youssef Street Joumayel Building - 1st floor Lebanon
1. Where the operation of the boiler must be familiar with the gas boiler operating standards and safety knowledge, certificate holder. Non-local staff is strictly prohibited to operate. Duty personnel should be strictly in accordance with the operating standards for gas boilers do a good job of running records and shift records, shift shift equipment and operation of the security situation should be submitted to the end. Check the boiler to ensure that the boiler is in good condition.
2. Boilers and safety accessories should be inspected and qualified, and within the validity period.
3. Kai furnace preparation
① gas furnace check whether the gas pressure is normal, not too high or too low, open the supply of oil and gas door section; ② check the pump is Sheung Shui, or open the release valve until Sheung Shui so far. Check the water level, the water level should be in the normal position, water level meter, water level color plug to be in the open position, put an end to false water level, if the water level, if the water level should be in the normal position, ⑤ check the control cabinet on the various knobs are in the normal position; ⑥ check the steam boiler water valve should be in the off state (see Figure 1); ④ check the pressure on the pipe valve must be open, the flue on the wind board must be fully open; , Hot water boiler circulating pump outlet valve should also be closed; ⑦ check whether the normal operation of softened water equipment, soft water to produce a variety of indicators are in line with national standards.